Overview: This industrial brackish RO equipment was constructed to treat well water and reduce the TDS for general use in a mall in Kuwait.
Industry: General Use
This equipment included a RO model #BW-600K-13780-8 from our RO-500 Series in addition to a Multi-Media Filter model #MLF-72 from our MF-1000 Series.
- (13) FRP pressure vessels Protec rated at 300 PSI model PRO-8-300-MSP-7
- (91) 8" TFC spiral wound membranes Hydranautics ESPA2-LD
- ORP on feed line and pH on product line
- Low- & high-pressure switches
- Paddlewheel flow meters
- Two high pressure pumps CRN90 with 2 VFDs
- Two 5-micron pre-filter with SS housing (SSC-88-316)
- Siemens S7-1200 PLC controller with HMI screen
Water Concern: Public facilities like malls or entertainment centers require water for general human use. These applications range from drinking fountains to toilet water. Therefore, a systemic water filtration system would best suit the requirements for all the applications. Supplying water from a well source usually includes an abundance of elevated parameters. The concern for this customer was reducing the TDS levels to accommodate the intended applications of the facility. This customer had a well water supply that contained 8,000 PPM TDS and was looking to produce 600,000 GPD.
Applied Solution: This industrial brackish RO equipment was recommended and constructed for a public mall facility in Kuwait. The capacity of this RO equipment was 600,000 GPD and the product is intended to be the main supply of water for the facility. This system includes the necessary pre-treatment and post-treatment units that keep the RO equipment functioning efficiently without any problems. Part of this pre-treatment is duplex multimedia filter to reduce turbidity and suspended solids. The pre-treated water continues on to a 5-micron cartridge filter to further reduce any leftover suspended solids and is injected with sodium metabisulfite along with antiscalant for chlorine reduction prior to reaching the RO membranes. Then, the water is pressurized by high-pressure pumps through the RO membranes that will raise the pressure to 300 PSI. The water exiting the system results in a product and reject stream.
Low operating cost, compact size, reduced footprint, and high quality production of freshwater.
Industrial Brackish RO Equipment for General Use 600,000 GPD - Kuwait - Data Sheet[/custom-documents]
Industrial Brackish RO Equipment for General Use 600,000 GPD -...
Pure Aqua designs and manufactures reverse osmosis and water t...
Pure Aqua designs reverse osmosis systems for global water nee...
Commercial Reverse Osmosis Purifier for Hotel 15,000 GPD - Gha...
Nice clean design and I like how they arranged the racks of vessels and piping. The actual RO system is even better than the 3D drawing that we saw.